|Place of Origin:||China|
|Minimum Order Quantity:||1|
|Delivery Time:||7 days|
|Payment Terms:||T/T,Western union|
|Material:||PE||Product Name:||Eye Wash|
|Original Water:||Drinking Water Or Filtered Water||Name:||Portable Eye Wash|
|Keywords:||Emergency Eye Wash Bottle,Emergency Eyewash Bottle,Moisturizing Face Cream||Feature:||Portable,Wall Mounted|
|Weight:||9KG||Easy To Carry:||Less Weight Easy To Use|
|Usage:||To Reduce The Level Of Injury,Eyewash & Shower Option For Almost Every Industrial Situation,Cleanroom Protection||Production Standard:||American ANSIZ358.1-2014|
Emergency shower,Eyewash,eye wash,Eye wash stations,eye washing,safety showers,eye wash solution,bradley eye wash,Emergency eye wash station,Emergency safety shower,Eye safety,eye washer,
Personal Protective Equipment:Emergency shower & Safety eye wash,Drench shower,Safety shower,Face wash bath,Eyewash station,Emergency shower.OSHA,ANSI Z358.1-2004,CE certificate.ISO9001:2008.
Portable Gravity Fed Eyewash(SH53L)
(Retractable Tray Eye Washes and Cart)
Portable press-wash skin & eye wash is not only the essential equipment of labor protection,but also the essential protective facilities against poisonous and corrosive material.It can be used in the field of the chemical industry,semi-conductor,metallurgy,electron and machine,also can be used in outdoor.
Place anywhere a water supply isn't available--such as outdoor work sites or remote plant locations. Polyethylene construction.
Specifications: Pull the tray down and a second later corrosion-resistant ABS plastic heads release a steady 15-minute flow. Two rugged carrying handles. 10-gal. functional capacity (14-gal. total).
Total Volume:14 Gallon(53L)
Functional Volume:16 Gallon(60L)
Flow Rate: 0.4 gpm for 15 minutes.
Compliance: ANSI Z358.1-2014. CE certified.
Step 1:self gravity fed eyewash euiqment shall be visually checked to determine if flushing flluid needs to be changed or supplemented.
Step 2:take proper precautions to help prenvent the growth of potentially harmful bacteria in eyewash tanks.we recommend either of the following procedures:
1. a. Tank empty.Refill tank.
b.Obstruction in line or fitting.Clesn obstruction.
|2.Poor flow from eyewash heads.||
2. a. Tighten head assembly.
b.Check for obstructions. If necessary, remove eyewash heads, clean and reassemble. To reassemble head, place cap screw through head and thread into head anchor two or three turns. Tilt head assembly and work anchor legs into eyewash armholes. Tighten assembly. Cheak for leaks.
3.Water leak between joints or fittings.
3. a. Pull hose off fitting. Smooth raised plastic edge on center of fittings.Return hose and hose clamp to original position.
b. Tighten hose clamps with pliers.