|Place of Origin:||China|
|Minimum Order Quantity:||1PC|
|Delivery Time:||7 days|
|Payment Terms:||T/T,Western union|
|Type:||Combination Shower And Eye Wash||Qty:||1pc/ctn|
SH712BSF-Pedaled shower & eyewash station,SS304,combination foot operated type
Product name:Pedaled shower & eyewash station,SS304
Material:304 stainless steel
Coating:High gloss epoxy powder,red/yellow is available
Sprayer head:ø250mm,has dust shield cap,can be removed when eye wash operated
Valve:eye wash-1/2" & shower-3/4" ball valve;activated in 1 second
Foot treadle:SS304,is available
Diameter of Eyewash Basin:260mm
More details,pls visit www.labppe.com
Emergency shower,Eyewash,eye wash,Eye wash stations,eye washing,safety showers,eye wash solution,bradley eye wash,Emergency eye wash station,Emergency safety shower,Eye safety,eye washer,
Personal Protective Equipment:Emergency shower & Safety eye wash,Drench shower,Safety shower,Face wash bath,Eyewash station,Emergency shower.OSHA,ANSI Z358.1-2004,CE certificate.ISO9001:2008.
|2||Shower pull rod||1set|
|3||Shower Inlet Erect Pipe||1set|
|4||Drain Erect Pipe||1set|
|5||Eye Wash Sprayer||1set|
|6||Eye Wash Bowl||1set|
|7||Eye Wash Switch||1set|
This unit is not only the essential equipment of labor protection, but also the essential facilities against poisonous and corrosive material. If accidents happen, reduce the damage to the minimum degree by quickly spraying or washing the hurt.
*Main function parameters
Choosing these data is considering the hurt to the skin, eye(s), when accidents happen.
1. with thread pipe and union connected, installed conveniency
2. The ball valve controls shower and eye wash respectively. It is easily operate and you may assure the quality.
3. the small drain hole in the eye wash pipe can drain off water remained in eye wash sprayers ,which is convinent for cleaning and preventing frostbite.
*Main material: good quality 304 stainless steel ,plishing/powder coating.
1. You should check the model, instruction and packing list of products before installation.
2. The location of the emergency equipment should be installed within 10 seconds walking time or 15 meters from the hazard.
3. clean the pipes before installed emergency shower.
4.pls install all parts according to the product drawing,the connect thread of every part must wind by sealing strip,connect inlet and outlet pipe separately.
5.check the switch valve wether they are flexible and exact.
*Method of application
1. Please pull down the shower pull rod, when you need shower,; push up pull rod, it will be close.
2. Please push the board clockwise, when you need eye washing, and the facility will work, pullback the push board withershins, eye wash valve close.
1. Should using the facility above zero environments, and you should notice the pipeline antifreeze if used in the cold place.
2. please clean the inet pipeline before installation.
3. suggest to install the main valve in the inlet pipe, close the main valve first after using, and close the shower/eye wash valve when clear up the remain water.
*The conk out and solutions
The flux of shower
A the diameter of inlet pipe is small
B the filter has foreign objects
A change the inlet pipe
B clean the stem objects
|2||The flux of eye wash sprayer is small||
A the adjustment rob is overdo
B the adjustment valve is blocked
A turn the rob anti-clockwise
B wash the valve
|3||The flux of eye wash sprayer is large||The adjustment rob is under-do||Turn the rob clockwise|
|4||The water remained in the basin is too more||The outlet is blocked||clean the stem objects|