|Place of Origin:||CN|
|Minimum Order Quantity:||1|
|Packaging Details:||WOODEN CASE|
|Material:||304 Or 316 Stainless Steel||Product Name:||Stainless Steel Emergency Shower & Eye Wash,mergency Shower Double Eye Wash|
|Original Water:||Clean Or Leached Water,Drinking Water Or Filtered Water,and Pay Attention To Quality Guarantee Period||Application:||Lab Equipment,oil|
|Name:||Manufacturer China Vertical Safety Shower And Eye Wash Station,Safety Emergency Body Shower Eye Wash Station||Color:||Silver|
|Function:||Safety Shower And Eyewash Station||Usage:||Eyewash & Shower Option For Almost Every Industrial Situation|
|Standard:||ANSI Z358.1-2009||Flow Control:||Eyewash Flow≥11.4L/Min,shower Flow≥75.5L/Min|
|Feature:||Valve Can Be Fully Opened Within 1 Second By Hand||Maximum Water Pressure:||7 Bar|
|Working Temperature:||0℃-55℃||Surface Treatment:||Polish Or High Gloss Epoxy Powder Coat|
|Sprayheads With Protective Covers:||Yes|
SH786B-Emergency shower & eyewash booth,stainless steel with water/waste tank and curtain
Product name:Emergency shower & eyewash booth,stainless steel with water/waste tank
Material:304 stainless steel plate;SS304
Sprayer head:,has dust shield cap,can be removed when eye wash operated
Valve:eye wash-1/2" & shower-1" ball valve;activated in 1 second
Waste tank and Water tank is available(1-2000L).
The emergency eye washer have already been adopted extensively by the most factories and the laboratories of the developed industrial countries of foreign countries,it is the indispensable apparatus of the security and the labour protection. It can make use of reducing the injure of acid,alkali, organic matter and other poisonous corrosive material. It can be extensively apply to petrochemical industry chemical industry, semiconductor industry, medical manufacturing industry, etc.
*Main function parameters
Choosing these data is considering the hurt to the skin, eye(s), when accidents happen.
1. The ceramic and ball valve controls spray and eye wash respectively. It is easily operate and you may assure the quality.
2. The spray head: using the ABS and brass to mould, coming to incorporate, in-built the spumes instrument, having filtration cotton and dust shield, the dust cup can clean the dust usually, removed automatically when eye wash is operate, to debase the hydraulic pressure when to be open abruptly, so as to protect eyes.
2.Pipe:galvanization steel pipe with resistant to rust in the inside of pipe.
3.eye wash bowl and shower sprayer head :ABS.
*Installation and maintenance
1. You should check the type of products, nstruction and the packing list for another time.
2. The location of the emergency equipment should be installed within 10 seconds walking time or 15 meters from the hazard.
3. Assembling the various components referring to sketch map, the contaction between various components needed to wind sealing belt, connected water source according to the diameter of inlet pipeline and outline pipeline.
4. After connecting the drain pipe, to see whether it moves well.
*Method of application:
1. Please pull down the pull rob, when you need shower, and the shower sprayer will open, when push up the pull rob, the shower sprayer will shut-off.
2. Please push the board clockwise, when you need eye washing, and the eye wash sprayer will work; when pullback the board widdershins, the eye wash sprayer will shut-off.
1. This facility is just used for emergency washing, do not use for shower. Please check the facility according to the rules and regulars. Make sure the facility will work well when there are accidences.
2. Activate shower at least weekly, to ensure the equipment dependability and validity. This equipment can not provide medical treatment; it can just reduce the hurt to the minimum degree by washing.
3. When an accident happens, please decide the showering time according to the hurt and prepare the medical treatment.
*The conk out and solutions
The shower outlet
flux is small
A the diameter of inlet pipe is small
B the filter has foreign objects
A change the inlet pipe
B remove the foreign objects
The eye wash sprayer
outlet flux is small
A the adjustment rob is overdo
B the adjustment valve is blocked
A turn the rob anti-clockwise
B wash the valve
|3||The eye wash sprayer outlet flux is large||The adjustment rob is under-do||Turn the rob clockwise|
|4||The seep in the basin is more||The outlet is blocked||Remove the foreign object|