|Place of Origin:||China|
|Minimum Order Quantity:||1|
|Delivery Time:||7 days|
|Payment Terms:||T/T,Western union|
More details,pls visit www.labppe.com
SH711BS-Stand eye wash Erect safety eye wash made of SUS304 meets ANSI
Product name:Eye wash station,SS304
Material:304 stainless steel
Sprayer head:has dust shield cap,can be removed when eye wash operated
Valve:1/2" ball valve;activated in 1 second
This unit is not only the essential equipment of labor protection, but also the essential facilities against poisonous and corrosive material. If accidents happen, reduce the damage to the minimum degree by quickly spraying or washing the hurt.
*Main function parameters
|Body shower||Eye wash||Tepid water|
Choosing these data is considering the hurt to the skin, eye(s), when accidents happen.
2.SS ball valve and screw seal controled shower and eye wash separately.
3.Set the seepage hole in the pipe of eye wash that can drain off the residual water,which clean pipe to prevent rust.
*Main material: SUS304 stainless steel
*Installation and maintenance
1. You should check the type of products, certificate of approval, instruction and the packing list for another time.
2. The location of the emergency equipment should be installed within 10 seconds walking time or 15 meters from the hazard.
3. Installation and maintenance:
A.connect the T-piece stainless steel pipe of outlet,inlet,body shoer pipe ,then connect with the bracket.
B.fix the shower handle and shower head on the stainless steel pipe.
C.connect the eye wash bowl with body stainless steel pipe.
D.intal the eye wash shower into the pipe through eye wash bowl.
E.instal the push board and foot treadle.
F. choose the raght place to connect the pipe of water inlet and fix the bracket tightly.
G.The adjust valve is in the middle of the two sprayers which can adjust the flux. It may need to adjust because of the different pressure and flux; though we adjust it before delivering you. The method of adjust: unscrew the helmet, adjust the adjustive pole with screwdriver, and turn it clockwise, the flux will be small, and turn it widdershins, the flux will be bigger.
*Method of application
1.Pull the shower handle down ,the body shower will work.
2.Please push the board clockwise, when you need eye washing, and the facility will work, pullback the push board withershins, eye wash valve close.
1. Should using the facility above zero environments, and you should notice the pipeline antifreeze if used in the cold place.
2. please clean the inet pipeline before installation.
3. suggest to install the main valve in the inlet pipe, close the main valve first after using, and close the shower/eye wash valve when clear up the remain water.
*The fault and solutions
The eye wash shower
outlet flux is small
A the adjustment rob is overdo
B the adjustment valve is blocked
A turn the rob anti-clockwise
B wash the valve
|2||The eye wash shower outlet flux is large||The adjustment rob is under-do||Turn the rob clockwise|
|3||The seep in the bowl is more||The outlet is blocked||Remove the foreign object|
Material: Stainless Steel
Color: Blue,Yellow,White,Customized Color,Red and black
Product name: Factory Price Emergency safety shower & eye wash with foot pedal,Safety Emergency Eye wash Shower,Eye wash station,eye wash recipe,hot sale pedestal mount stand eyewash stations
Application: chemical/laboratory/research institution,Clean Room.industry,General purpose,medical,food service