|Place of Origin:
|Minimum Order Quantity:
|Stainless Steel,SS304(carbon Steel Or Ss316L Is Optional)
|Stainless Steel Emergency Shower & Eye Wash
|Drinking Water Or Filtered Water
|Safety Emergency Body Shower Eye Wash Station
|Green/ Yellow/ Silver
|Safety Shower And Eyewash Station
|Eyewash & Shower Option For Almost Every Industrial Situation
|Eyewash Flow≥11.4L/Min,shower Flow≥75.5L/Min
|Strong Corrosion Resistance&easy Operation,Valve Can Be Fully Opened Within 1 Second By Hand
|Maximum Water Pressure:
|Polish Or High Gloss Epoxy Powder Coat
|Sprayheads With Protective Covers:
SHD200SG-Pedaled safety shower & eyewash,sound and light alarm and signal upload system
Product name:Foot Control Stainless Steel Combination Eye Washes/Shower (with the Platform)
Material:304/316 stainless steel
1.Head: 10″ABS plastic in Safety Yellow, ABS plastic eye wash.
2.Valves: Shower valve is making of the 1″SS304 ball valve. Eye wash valve is making of the 3/4″valve.
3.Water supply and outlet: 1-1/4″IPS.
4.Flow control: 114L/Max.
5.Hydraulic pressure: 0.2MPA~0.8MPA
6.Original waster: Clean or leached water.
7.Operation condition: Eye Wash & Showers option for almost every industrial situation.
8.Notification of operation: Use in the lower polluted chemical environment. Please choose the SS316 when the acidity is too high
More details,pls visit www.labppe.com
Sound and ligh alarm, fixed on the shower pipe top, and sound and light alarm signal upload works: When someone uses the shower or eyewash system, the pipe water flow, start flow switches, flow switches at the same time to sound and light alarms and signals Upload turned on or off signal, sound and light warning lights turned on or off, start or stop the alarm; the flow switch to the control center at the same time a passive dry contact signal (ON or oFF signal), the control center received on or off signal to start or stop the alarm.
sound and light alarm and signal upload works: When someone uses the shower or eyewash system, the pipe water flow, start flow switches, flow switches at the same time sound and light alarms and signals to connect or disconnect signal upload, audible alarm lights turn on or off to start or stop the alarm; the flow switch to the control center at the same time a passive dry contact signal (ON or oFF signal), the control center receives on or off the signal to start or stop the alarm.
Is a sound and light alarms installed in the field of sound and light alarm device, when the fire scene and confirmed, installed in the field by the fire alarm sound and light the fire control center fire alarm controller starts, sending a strong sound and light alarm signal to remind the site personnel in order to achieve the purpose.
The use of sound and light alarms sound chip amplification by the transistor and transformer, push speaker audible; the timing circuit control using ultra-bright light-emitting diodes emit flashes of light signals. When the fire scene and confirmed, the fire alarm sound and light installation at the scene by the fire control center of fire alarm control linkage program starts.
Sound and light alarms are named according to the alarm from the way named Oracle security alarm equipment factory audible alarm means when it finds intruder alarm emits a high decibel alarm sound, lights flashing simultaneously used to deter thieves reminder tenants, neighbors, the security role of the illegal invasion.
Sound and light alarm general and infrared detectors, door composed sound and light anti-theft alarm system, door sensor to detect when the infrared detector or intrusion immediately send an alarm signal when the alarm to sound and light, sound and light alarm immediately alarm.
Sound and light alarms for use in hazardous locations is to send a warning signal will not ignite explosive gas alarm signal means to the people through a variety of sound and light, it can simultaneously send out sound and light two kinds of alerts signal.
Note audible alarm installed
(1) Alarm probe sensing element is mainly catalytic combustion gas sensor, a platinum wire coil wrapped in adhesive composition of alumina and the spherical outer surface with platinum, palladium and other precious metals. Therefore, the installation must be careful to avoid broken probe.
(2) alarm installation height should generally be in 2038-2438cm, in order to carry out routine maintenance on the maintenance staff.
(3) The alarm is safe instruments, sound, light display, should be installed in the staff easy to see and easy to hear the place, in order to promptly eliminate hidden dangers.
(4)Around the alarm can not have an impact on the instrument work strong electromagnetic fields (such as high-power motors, transformers).
(5) Differentthe measured gas density, the installation position of the indoor probe should also be different. When measured gas density is less than the density of air, the probe should be installed at a distance of 30cm roof, the downward direction; on the contrary, the probe should be installed at 30cm from the ground, upward direction.
The above is information about precautions audible alarm works and sound and light alarm installed, I hope we can be of better use in life, and hope that we can make better use of sound and light alarm.