|Place of Origin:||China|
|Minimum Order Quantity:||1|
|Delivery Time:||7 days|
|Payment Terms:||T/T,Western union|
|Brand Name:||Techsafe||Material:||Galvanization Iron|
|Product Name:||Laboratory Safety PPE Emergency Shower Eye Wash||Size:||Combination|
More details,pls visit www.labppe.com
SH712B-Safety shower & eyewash station,Carbon steel,yellow color
Product name:Safety shower & eyewash station,Carbon steel,yellow color
Coating: High gloss epoxy powder coating
Shower: 1"IPS valve, hands-free stay-open valve activates in 1 second for body rinse
Eye Wash: 1/2"valve, ergonomically designed for eyes, face, and hands wash, hands-free
Spray Head: Nylon, remove impurities from water
Water supply and outlet:1"IPS.
Hydraulic pressure: 0.2MPA~0.8MPA
Emergency shower,Eyewash,Personal Protective Equipment:Emergency shower & Safety eye wash.OSHA,ANSI Z358.1-2004,CE certificate.ISO9001:2008.
|2||Shower Switch Handle||1set|
|3||Shower Inlet Erect Pipe||1set|
|4||Drain Erect Pipe||1set|
|5||Eye Wash Sprayer||1set|
Eye Wash Bowl and
Emergency eye wash instruction
This unit is not only the essential equipment of labor protection, but also the essential facilities against poisonous and corrosive material. If accidents happen, reduce the damage to the minimum degree by quickly spraying or washing the hurt.
*Main function parameters
Choosing these data is considering the hurt to the skin, eye(s), when accidents happen.
1. with thread pipe and union connected, installed conveniency
2. The ball valve controls shower and eye wash respectively. It is easily operate and you may assure the quality.
3. the small drain hole in the eye wash pipe can drain off water remained in eye wash sprayers ,which is convinent for cleaning and preventing frostbite.
*Main material: good quality 304 stainless steel
1. You should check the model, instruction and packing list of products before installation.
2. The location of the emergency equipment should be installed within 10 seconds walking time or 15 meters from the hazard.
3. clean the pipes before installed emergency shower.
4.pls install all parts according to the product drawing,the connect thread of every part must wind by sealing strip,connect inlet and outlet pipe separately.
5.check the switch valve wether they are flexible and exact.
*Method of application:
1. open the inlet control valve before using.
2. open the eye wash dust cove upwards at the handler,eye wash sprayer works.
3.pull down shower switch handle ,body shower can spray water.
1. open or close the eye wash bowl dust cover gently.
2. Should using the facility above zero environments, and you should notice the pipeline antifreeze if used in the cold place.
3. suggest to install the main valve in the inlet pipe, close the main valve first after using, then close the shower/eye wash valve when clear up the remain water.
1.only can use when accident happen,no using for body and hands washing in normal.
2.Test the equipment competely every week,so we can ensure emergency use when accident happen.this equipment is not medical equipment,only can emergency shower and reduce hurts to body by hazardous material.
3.when accidents happen,hurt people should choose shower time according by hurt degree,and prepare salvage steps at the same time.
*The conk out and solutions
|1||Water remain in the eye wash bowl is too more.||The drain hole is blocked in the eye wash bowl or outfall sewer is blocked||
Clean the stem object
|2||Eye wash dust cover and eye wash switch valve can not close completely||
A power of spring is too small
B the screw nuts in pivots are loose
A replace spring
B pull the eye wash switch valve link and dust cover pivots screw,when switch valve and dust cover close fully,screw the screws tightly.
|3||Flux of water is small||
A the dia.of inlet pipes is small, the pressure is small
B filter screen of shower is blocked.
A enlarge the dia. Of inlet pipes or add pressure increasing valve
B screw off shower head,clean the filter screen