|Place of Origin:||China|
|Minimum Order Quantity:||1|
|Delivery Time:||7 days|
|Payment Terms:||T/T,Western union|
|Material:||Stainless Steel||Product Name:||Eye Washer|
|Type:||Wall Mounted Eye Wash Station||Usage:||Laboratory And Factory|
|Color:||Silvery||Name:||Wall Mounted Emergency Eye Washer|
|Standard:||ANSI Z358.1-2009||Feature:||Valve Can Be Fully Opened Within 1 Second By Hand,wall Mount|
|Application:||Emergency Face And Eye Wash,Clean Room||Original Water:||Drinking Water Or Filtered Water|
|Keywords:||Emergency Eye Wash||Valve:||1/2"corrosion Resistant Brass Galvanized Ball Valve|
|Hydraulic Pressure:||0.2MPA-0.8MPA||Eye Washer Bowl:||Stainless Steel / PP Bowl|
SH359DB-Wall mounted SUS304 eye wash ANSI CE
Product name:Wall mounted eye wash,SS304
Material:1.body-304 stainless steel;2.bowl-PP;3.eye wash nozzle-brass
Sprayer head:has dust shield cap,can be removed when eye wash operated
Switch:1/2" ball valve;activated in 1 second.
More details,pls visit www.labppe.com
Emergency shower,Eyewash,eye wash,Eye wash stations,eye washing,safety showers,eye wash solution,bradley eye wash,Emergency eye wash station,Emergency safety shower,Eye safety,eye washer,
Personal Protective Equipment:Emergency shower & Safety eye wash,Drench shower,Safety shower,Face wash bath,Eyewash station,Emergency shower.OSHA,ANSI Z358.1-2004,CE certificate.ISO9001:2008.
Wall Mounted Eye Washer Instuction(SH359C/D)
Please check the quantity of the fittings according to the following lists after unpacking,check whether there is damage transport, if there is any question or qualitative deficiencies,please get in touch with the local franchiser of our company or our company immediately,you will receive the satisfactory reply.
|1||Eye Wash sprayer head||1 set|
|2||Eye wash bowl||1 pc|
|3||Main Body||1 set|
|4||Wall Mounted Bracket||1 pc|
|5||Switch Push Board||1pc|
The emergency eye washer have already been adopted extensively by the most factories and the laboratories of the developed industrial countries of foreign countries,it is the indispensable apparatus of the security and the labors protection. It can make use of reducing the injure of acid,alkali, organic matter and other poisonous corrosive material. It can be extensively apply to petrochemical industry chemical industry, semiconductor industry, medical manufacturing industry, etc.
*Defining for eye wash
As the splash of chemical liquid taking place to staff member's body, face, eyes or the staff members’ clothes cause the fire, it is the effective safe protection articles to minimize the dangerous.
*Main performance parameter
|Pressure grade MPa||Flux L/min||Applicable condition|
|Nominal pressure||Sealed pressure||Working pressure||
|Pure water of normal atmospheric temperature or according with the sanitary standard|
The choice of the main performance parameter according to USA ANSI Z358.1-2004, in order to lighten harmful substance to human skin, eyes injury of top layer and simulate when accidents make happened.
1.Making use of the ball valve to control the eye wash. Easy to operate,open and close it fast , it is reliable to close.
2.The flux regulation and control valve can regulate by oneself. (Regulation method can refer to installing and debugging).
1. The material of main body is 304 stainless steel.
2. Eye wash bowl: 304 stainless steel.
3. Eye wash head:ABS.
*Installing and debugging
1. Must re-inspect the type of the products, certificate of quality, operation instructions, case the list before installation.
2. The installation site should from within the accident lively to suffer from 15 meter, in order to run 10 second within the place can reach.
3. Install stand of wall: draw the punch position according the wall screw hole, install M10 swell screw to fix the wall stand.
4. Connect the body part: part of body and flat of wall connected byG1¼ Screw Nut (the 5TH) and screw on. And then connect the bowl and the eye-washing sprayer head.
5. Put through into the water pipe, drain pipe. Check whether the ball valve switch is flexible, is put in place; has phenomenon of locking.
Please push the board clockwise, when you need eye washing, and the eye wash sprayer will work; when pullback the board widdershins, the eye wash sprayer will be shut-off.
1. This facility is just used for emergency washing, do not use for shower. Please check the facility according to the rules and regulars. Make sure the facility will work well when there are accidences.
2. Activate shower at least weekly, to ensure the equipment dependability and validity. This equipment can not provide medical treatment; it can just reduce the hurt to the minimum degree by washing.
3. When an accident happens, please decide the showering time according to the hurt and prepare the medical treatment.
*The conk out and solutions
The shower outlet
flux is small
A the diameter of inlet pipe is small
B the filter has foreign objects
A change the inlet pipe
B remove the foreign objects
The eye wash sprayer
outlet flux is small
A the adjustment rob is overdo
B the adjustment valve is blocked
A turn the rob anti-clockwise
B wash the valve
|3||The eye wash sprayer outlet flux is large||The adjustment rob is under-do||Turn the rob clockwise|
|4||The seep in the basin is more||The outlet is blocked||Remove the foreign object|
Material: Stainless Steel
Product name: Eye Wash Station,Eye Washer,normal sterile saline solutions,Industrial Emergency Safety Shower,safety emergency shower eye wash
Type: safety shower and eye wash,wall mounted eye wash station,Wall Mounted
Usage: to reduce the level of injury,laboratory and factory,Equipment,eye or body washing,Cleanroom Protection